ATEX approved Static grounding &bonding clamp with 2 tips
Categories Grounding Clamp Album View larger image Brand ALPTEC Model SC-02 Material Aluminum Opening 28mm Dimensions 160mm X 86mm Weight 295g Certificate ATEX Unit Price US $ 18.5-23.1 / piece FOB port Qingdao Port or any port of china Terms of Payment L/C, Western Union, T/T, Paypal Download DOC Update Time 2021-03-02Detail Information
（1）ATEX approved reliable grounding clamps with 2 tips are ATEX approved .
（2）Die-cast aluminum construction with 2 stainless steel points.
（3）Static grounding &bonding clamp can be connected to an electronic apparatus together with a two-core cable.2. SpecificationsProduct nameATEX approved rStatic grounding &bonding clamp with 2 tipsBrandALPTECModelSC-02MaterialAluminumCertificateATEXOpening28 mmDimensions160 mm x 86 mmWeight295 g3. Details
ALPTEC Other Material Cast Aluminum Aluminum Scrap Body Thickness 12mm <10mm Tips Nichrome Stainless steel certificate ATEX No Spring Defend spring Simple spring4. ApplicationsRecommended application static earthing clamps for the system includes but is not limited to:1) Tank truck loading and railway loading.2) The equipotential connection of loading arms or oil pipeline.3) The transfer of the drums containing raw materials.Environment temperature:-40℃ to +60℃5. PackagePackaging: cartons(20 pcs in one carton)Dimensions:27*27*20 cmGross Weight: 6.0 kgsDelivery time: 2 days after shipmentDelivery:Shipping is depended on customers, either by sea or courier such as FedEx, DHL, TNT, UPS6. PrinciplePrinciple of SC and CC series: the spring and the clamp form the lever, with its strong pressure, the sharp and hardened contact points on the clamp head will penetrate the paint and rust. It ensures the effective connection of static electricity carrier and the ground. Principle of PC series: the inner side of the clamps bodies are Jagged, the tight locking force of the bolts forms strong pressure to penetrate the paint and rust. It ensures the effective connection of static electricity carrier and the ground.7.Sizes and Outline drawings8.Usage1. When using the SC series static grounding clamps, open the clamp, clip the clamp on the equipment to be grounded, shake the clamp to get rid of the paint or rust to ensure good contact. Open the clamp and remove it after using.2. When using the PC and CC series static grounding clamps, unscrew the bolt until the clamp can be fixed to pipes or flat materials, and then tighten the bolt to ensure good contact. Unscrew the bolt and remove the clamps after using.3. When using the PC and CC series static grounding clamps, fix one end according to the method above and then fix the other end.Related Products